Does HPS Have 5% Impedance Centurion® R Reactors at 690 Volts?
Not based on standard motor current ratings. A 5% Z 600 volt reactor will have 4.3% Z impedance at 690 volts. If higher than 4.3% is required, please consult HPS. Often two reactors can be wired in series to provide higher impedance ranges.