Can I increase the kVA rating of an existing transformer?
The most common way to increase the available kVA rating of an existing transformer is to add additional fan cooling. This typically requires modifications including raising the transformers core, adding fans and fan brackets, a motor power supply and controls to start fan cooling when the transformer’s components reach a preset temperature. Fans should never be added without contacting and following specific instructions from the manufacturer. Low temperature rise transformers (115C and 80C rise with 220C insulation) can maintain higher loads in lower ambient transformers. Always follow proper ventilation and clearance instructions.